|Lamp Type: Metal Halide||Class 1 Division 2 Groups A, B, C, D|
|Dimensions: 7"-Depth,20 3/4"-H,17"W||UL 844 Hazardous Location|
|Watts: 1000||UL1598 Wet Locations|
|Voltage: 120V, 208V, 240V, or 277V||UL 1598A Outdoor Marine Approved|
|Lighting Configuration: Flood Pattern||NEMA 4, 4X|
|Mounting: Adjustable Trunnion Bracket||IP56 to IP66|
|Weight: 29.7 lbs||Bulb NOT Included|
|Total Lumens:Â N/A||Â|
|Wiring:Â 3/4 inch Threaded Entrance|
Made in Texas
The extremely durable Larson Electronics HALSS-TRN-1000W-MH metal halide hazardous area light produces exceptional illumination from a 1000 watt metal halide lamp. Constructed of corrosion resistant stainless steel and U.L. listed for marine use, this fixture is a versatile and ideal hazardous area lighting solution for areas where wet or corrosive environments are encountered.
The rugged HALSS-TRN-1000W-MH metal halide fixture is weatherproof and suitable for use in wet, outdoor and marine environments making it an ideal lighting solution for industrial applications, boat docks, building exteriors and outdoor work areas. The lamp housing is weatherproof and constructed of stainless steel, featuring a removable front-access door with captive closure screws for easy servicing.
The optical assembly includes heat/impact-resistant tempered door glass with a stainless steel door frame and heavy duty, high temperature silicone rubber seal. The lamp socket is a specification grade mogul base porcelain unit with heavy gauge brass, a nickel-plated, double lamp-grip screw shell and spring-loaded center contact.
Make all electrical connections in accordance with the National Electrical Code and any applicable local code requirements. Verify that supply voltage is correct by comparing it to nameplate. Three-conductor No. 14 cable (with 90Â° C minimum insulation) is recommended for making electrical connections. Wiring is accomplished through the wiring box provided on the fixture. The box is provided with a size 3/4-in. NPT threaded conduit opening. Wiring methods must comply with NFPA 70 (The National Electrical Code), Article 501 for Class I, Division 2 Hazardous (Classified) Locations. Â Please Note: This fixture does not include bulb. Please see related items for replacement lamp.
Shipping and delivery Information
Estimated delivery times range from 1 to 3 weeks, depending on your location, the product ordered and stock availability. External factors such as courier network disruptions can also impact delivery timelines. PuriLite strives to ship your purchase in the shortest possible time using industry standard courier services.
For any questions related to shipping and delivery, please call 1-844-787-5483, email us at email@example.com or chat with us by clicking on the chat icon at the bottom right of this page.
Your payment information is processed securely. We do not store credit card details nor have access to your credit card information.